# How to Calculate KW Requirements for Typical Heater Applications

Tank Heating Calculations

When selecting a heater for tank heating application you must first determine whether the application requires that the temperature be maintained or if the temperature needs to be raised.  Below are the calculations for each application.  You can also visit our website and utilize our online calculator; look for the free calculator link near the top of the page.

Maintain Temperature

To calculate the KW required to maintain the temperature of a tank you will need to determine the tanks surface area, process temperature to be maintained, minimum ambient temperature and the R-value of the insulation.

Surface area:

Round tank –

A (ft²) = (2 x p x r x h) + (2 x p x r²)

p = 3.14

r = radius (ft)

h = height (ft)

Rectangular tank –

A (ft²) = 2 x [(l x w) + (l x h) + h x w)]

l = length (ft)

w = width (ft)

h = height (ft)

After determining the tanks surface area the maintain KW can be calculated as follows:

KW = (A x (1/R) x ΔT(°F) x SF)/3412

A = surface area

R = R-value of the insulation

• Use 0.5 as the R-value of an uninsulated steel tank
• See the chart below for typical examples
• R-value = thickness (in.)/k-factor

ΔT = difference between the process set point temperature and lowest ambient temperature

SF = safety factor, recommended 1.2

3412 = conversion of BTU to KW

Table 1

 Insulation Type R-Value/inch of thickness Fiberglass R-3 Mineral fiber R-3.7 Calcium silicate R-2 Open-cell polyurethane foam R-3.6 Closed-cell polyurethane foam R-6 Polyisocyanurate spray foam R-6

Example:

A 42’ diameter x 40’ tall crude oil tank with R-6 insulation needs to be maintained at 75°F given a minimum ambient temperature of 10°F.

A = (2 x 3.14 x 21 x 40) + (2 x 3.14 x 21²)

A = 8044.68 ft²

KW = (8044.68 x 1/6 x 65 x 1.2)/3412

KW = 30.65

Raise Temperature

The KW calculation to raise the temperature of a material in a tank (heat-up) starts with the same information required in the maintain application.  Additionally we’ll need the weight of the material to be heated, the specific heat of the material and the time required to heat the material from its start temperature to its end temperature.  The KW calculation to raise the temperature is as follows:

KWtotal = KWheat-up + KWmaintain

KWheat-up = [(M x Cp x ΔT x SF)/3412]/t

M = weight of the material in pounds

Cp = Specific Heat, see examples in the chart

ΔT = difference between the process set point (end) temperature and the start temperature

SF = safety factor, recommended 1.2

3412 = conversion of BTU to KW

t = time in hours

KWmaintain = (A x (1/R) x ΔT(°F) x SF)/3412

A = surface area

R = R-value of the insulation

• Use 0.5 as the R-value of an uninsulated steel tank

ΔT = difference between the process set point temperature and lowest ambient temperature

SF = safety factor, recommended 1.2

3412 = conversion of BTU to KW

Example:

A 4’ x 6’ x 12’ tank with 1800 gallons of water needs to be heated from 60°F to 95°F in 3 hours.  The tank has R-4 insulation and the minimum ambient temperature is 0°F.

To begin we need to convert the gallons of water to pounds:

lbs = G x D1

G = gallons

D1 = lbs per gallon from the chart below

lbs = 1800 x 8.34

lbs = 15,012

If the volume of the tank is stated in cubic feet (ft³) the formula looks like this:

lbs = C x D2

C = Cubic feet of material

D2 = lbs per ft³ from the chart below

Table 2

 Material D1 lbs/gallon D2 lbs/ft³ Specific Heat water 8.34 62.4 1 #1 fuel oil 6.8 50.5 0.47 #2 fuel oil 7.2 53.9 0.44 #3,4 fuel oil 7.5 55.7 0.425 #5,6 fuel oil 7.9 58.9 0.41 Bunker C 8.15 61 0.5 SAE 10-50 weight oil 7.4 55.4 0.43 ethylene glycol 9.4 70 0.55 50% ethylene glycol/water 8.8 65.8 0.76 air – 0.073 0.24 nitrogen – 0.073 0.25

KWheat-up = [(15,012 x 1 x 35 x 1.2)/3412]/3

KWheat-up = 61.6

plus

KWmaintain = (288 x 1/4 x 95 x 1.2)/3412

KWmaintain = 2.4

KWtotal = 64

Calculations for heating air in a duct

Once the volume of air in standard cubic feet per minute (SCFM) and the required temperature rise in °F (ΔT) are known, the required kilowatt rating (KW) of the heater can be determined from the following formula:

KW = (SCFM x ΔT)/3193

Note that CFM is given at standard conditions (SCFM): 80° F and normal atmospheric pressure of 15 psi. The CFM at a higher pressure (P) and inlet air temperature (T) may be calculated as follows:

SCFM = ACFM x (P/15) x [540/(T+460)]

Example:

A drying oven, operating at 25 psia (10 psi gauge pressure), recirculates 3000 CFM of air per minute through a heater which raises its temperature from 350 to 400° F.

To select an appropriate heater:

Step 1: Convert 3000 CFM at 25 psia and 350° F to CFM at standard conditions using the above formula:

3000 x (25/15) x [540/(350°F+460)] = 3333 SCFM

Step 2: Calculate the required KW:

[3333 SCFM x (400°F-350°F)]/3193 = 52 KW

Calculations for circulation heater applications

When calculating the power required to heat a material flowing through a circulation heater, the KW equation shown below can be applied.  This equation is based on the criteria that there is no vaporization occurring in the heater. The KW equation incorporates a 20% safety factor, allowing for heat losses of the jacket and piping, variation in voltage and wattage tolerance of the elements.

KW = (M x ΔT x x Cp x S.F.)/3412

Where:

KW = power in kilowatts

M = flow rate in lbs/hr

ΔT = temperature rise in °F (The difference between the minimum inlet temperature and maximum outlet temperature.)

Cp = specific heat in BTU/lb °F

S.F. = safety factor, 1.2

3412 = conversion of BTU to KWH

Water heating example:

We have 8GPM of water with an inlet temperature of 65°F and outlet temperature of 95°F.  First, convert the flow rate to lbs/hr.

 8 gal x 1 ft³ x 60 min = 64.17 ft³/hr min 7.48 Gal 1 hr

Convert to lbs/hr, obtain the density and specific heat from table 2 above.

64.17 ft³/hr x 62.4 lbs/ft³ = 4004 lbs/hr

Now calculate the KW:

 KW = 4004 lbs/hr x (95-65)°F x 1 BTU/lb °F x 1.2 3412 KW = 42

Gas heating example:

Air is flowing at 187 CFM and 5 PSIG pressure.  It needs to be heated from an inlet temperature of 90°F to an outlet temperature of 250°F.  First, convert the flow rate to SCFM using the formula given earlier.

187 x (20/15) x [540/(90°F+460)] = 243.7 SCFM

Convert to lbs/hr, again referring to table 2 for the density and specific heat.

 243.7 SFCM x 60 min x 0.073 lbs = 1067.4 lbs/hr 1 hr ft³

Now calculate the KW:

 KW = 1067.4 lbs/hr x (250-90)°F x 0.24 BTU/lb °F x 1.2 3412 KW = 14.4

If you enjoyed this post, please consider leaving a comment or subscribing to the RSS feed to have future articles delivered to your feed reader.
12 replies
1. proxy list says:

Hi,I check your blogs named “How to Calculate KW Requirements for Typical Heater Applications – Accutherm” like every week.Your humoristic style is awesome, keep doing what you’re doing! And you can look our website about proxy list.

2. preeti says:

good explanation on How to Calculate KW Requirements for Typical Heater Applications
you have given nice formula

3. Nasser says:

can I have the same Examples in Kg, Degree Celsius, KW, Meters,…. Dimensions system
my mail is
nshahbo@yahoo.com

4. BestLesli says:

I see you don’t monetize accutherm.com, don’t waste your
traffic, you can earn extra bucks every month with new monetization method.
This is the best adsense alternative for any type of website (they approve all websites),
for more info simply search in gooogle: murgrabia’s tools

5. Callum Palmer says:

We are wanting a new water heater. Once I figure out which one, I’ll have to do your calculations. That way, we can be sure that the KW for it will be correct.

6. unclefukerT says:

Guys, I gotta boast. I found a girl online who got naked for me. Just check this out: https://is.gd/HmQeh6

7. Tanveer Aslam says:

Like you blog .I want to learn in more detail.

8. Brijratan Chandak says:

Electrical heating calculation

9. spearcastwinder.best says:

Solo llevan la conversación, solo loate
a viejas espiritualmente desnudas que me decepciones eran con la manera con la que puedas comprobar que no reclamos accidentalmente
o bien atacarme. Afíncol. Pero aunque estas dos opcionesGratis se podrán contactar con personas y discutir con la intención de que tu no querer comprar meramente interesados.

Arago, por ejemplo. Todas los hombres sean en estos pasos son estos
trucos, tienen modelos en general y únete a las mujeres en parte de
temas que están intimidados por una persona son unsumido.
¿Nunca quiero cuarte un día entero en una dama para que tu día más te gué
te osará prueba un amor?
spearcastwinder.best https://spearcastwinder.best

10. Wayne Landry says:

How much KW will it take to raise 28 gravity oil from 80 deg F to 400 deg F and from 80 deg f to 750 degF…for 500 bbls a day rate

several of us are getting big variations of the KW from 26, 75-100 & 300Kw…big differences…someone is calculating incorrectly

11. Wayne Landry says:

Please call me…337-319-3779

12. Yogeshwar Raikohad says:

How to calculate the total kwh energy to heat up & maintain the ceramic fiber block furnace zone. furnace Side wall & top inside insulation thickness 300mm of ceramic fiber block and floor with insulating bricks and high temp ceramic module.

### Leave a Reply

Want to join the discussion?
Feel free to contribute!

This site uses Akismet to reduce spam. Learn how your comment data is processed.